Generator Service and Repair
Trusted Power Systems offers full generator service, repairs, and planned maintenance programs for residential, commercial, and industrial generator systems.
For Chicagoland area customers interested in scheduling a maintenance or service call with one of our trained technicians, please contact us directly at 312.462.3299.
WE SERVICE ALL GENERATOR MAKES AND MODELS up to 1Megawatt!
Manufacturers include Briggs & Stratton, Cummins, Onan, Generac, Kohler, GE, Winco, Baldor, Centurion, Rheem, Milbank, Guardian, Honeywell, Carrier, Honda, Katolight, Caterpillar, MTU, Gillette, Cutler Hammer, Eaton, and many more.
Generator Tune Up |Preventative Maintenance
A scheduled maintenance program ensures that your automatic standby generator is always in top operating condition and warranty requirements are being met. We recommend maintaining your generator annually. We have maintenance agreements we strongly suggest to keep your generator running at its best. Trusted Power Systems offers different levels of maintenance programs to meet your needs.
A complete maintenance service by one of Trusted Power Systems’ trained technicians includes the following:
- Oil Change
- Oil Filter Change
- Spark Plug(s) Change
- Air Filter Change
- Inspect Battery
- Generator Pad Check
- All Wiring Check
- All Gas Plumbing Check
- Inspect Transfer Switch Fuses, Mechanical Parts, and Wiring
- Inspect Transfer Switch Operation
- Calibrate Date/Time/Weekly Self Test
- Verify Engine RPMs
- Calibrate Generator Output Voltage
- Calibrate Generator Output Frequency
Inspection: (Recommended Interval – Every 6 Months)
74 point inspection covering critical items such as your engine, generator, and transfer switches. The full service also includes oil and oil filter replacement, fuel filter replacement and coolant filter replacement if applicable. Air filters will be checked but will only be changed if needed (only with approval from the customer).
Inspection Full Service: (Recommended Interval – Every 12 Months)
(If unit is used for Prime Power, recommend changing oil every 6 months or 250 hours, whichever comes first)
74 point inspection covering critical items such as your engine, generator and transfer switches. This full service also includes oil and oil filter replacement, fuel filter replacement and coolant filter replacement (if applicable). Air filters will be checked, but will only be changed if needed (only with approval from the customer.
Load Bank Testing: (Recommended Interval – Every 12 Months)
(Annual test is REQUIRED for Hospitals and other life support providers if a load of 30% of the generator set’s nameplate rating cannot be achieved during the required monthly test.)
Optional 2 or 4 hour testing. Minimizes potential of issues related to moisture build-up, settling of particles in fuel and carbon deposits in engine. This is not only a recommended test, but per JCAHO and Public Health regulations, is a requirement for facilities providing life support systems, i.e. hospitals and nursing homes.
Load Bank Testing on your generator system is suggested to be performed annually to ensure your system is ready for the largest loads. Load Bank Testing applies desired loads to your generator set to monitor the performance and tests the capabilities of your system. Performing this test ensures your system is setup to handle the load it was designed to achieve.
Trusted Power Systems offers Load Bank Testing on Generators units all the way up to 150kW currently for Single Phase and 3 Phase applications. Contact us for more information.
Coolant System Flush: (Recommended Interval – Every 24 Months)
Reduces sediment buildup which could cause corrosion in coolant piping and tanks.
Belts and Hoses Replacement: (Recommended Interval – Every 24 Months)
Replacement of belts and hoses reduces risk of failure which could cause further damage to engine.
Fuel Cleaning: (Recommended Interval – Every 24 Months)
Reconditions, stabilizes and decontaminates fuels. It efficiently removes water, sludge and sediments that naturally accumulate in tanks.
Battery Replacement: (Recommended Interval – Every 24 – 36 Months)
Batteries are load tested with carbon pile testing. Remove and replace batteries if between two and three years old at time of Inspection or full service Inspection. Includes disposal of old batteries.